Today’s video is an overview of theNEMA 1 AC Tech SMVector seriesvariable speed drive features, functions and specifications. TheNEMA 1 AC Tech SMVector seriesvariable speed drive comes equipped with a large amount of functionality including volts / hertz mode, vector mode, sensorless vector mode and advanced volts per hertz mode. There are a large number of built in features for current and line voltage protections as well as certifications for safety regulations such as UL.
In this video we give you a simplified answer to the question “What is a Variable Frequency Drive”
Variable Frequency Drives (VFDs) are also commonly known as adjustable frequency drives, adjustable speed drives, AC drives and inverters.Variable Frequency Drives have a wide range of application use and operate as load controls within these applications that may accomplish up to a 50% reduction in energy cost.
Thanks for viewing and remember that we sell and service bothVFDs and electric motors. You can always call us with any questions at 574-256-1000 or check out our website vfddistrbuting.com for product manuals, frequently asked questions and our Ebay Store.
In this video we go step by step in showing you how to land 120 volts onto your SMVector variable frequency drive. Ensure you are qualified to handle this electrical equipment before working on it. This process is both easy and painless. The tools you will need are a phillips head screwdriver, wire strippers, your power source leads, wire crimpers, terminal ends and of course, your Variable Frequency Drive (VFD). Feel free to ask us any questions you may have and don’t forget we both service and sell this equipment – you can contact us by telephone at 574.256.1000
Thank you all for stopping by. Today we are going to show you how to access the terminal strip on your AC Tech SMVector Series Variable Frequency Drive (VFD). This is a basic introduction to the drive itself and for those of you who have not worked with this product before. You will find doing this is both easy and intuitive – and remember, if you have any additional questions feel free to let us know. Do not forget, larger drives than the one depicted in this video will have a slightly different layout, but the concept will be the same.
For those of you who are familiar or unfamiliar with Lenze / AC Techs SMVector series drive they have come a long way since their conception. All AC Tech products are manufactured in Uxbridge Massachusettes. Today we discuss how to read the nameplate data off of the drive. It is not as complicated as most might think. This is a great way to determine what voltage inputs, frequencies, phases are required and how to determine whether the Variable Frequency Drive itself is an adequate enough size for the motor you want to connect to it. Enjoy!
It has become common knowledge that the poor economy is causing businesses all over the United States to suffer. As a result of the credit crunch, industrial manufacturing, automation, processing, and other related markets have been seeking alternatives, and found them online. Historically, industrial markets have relied heavily on the local businesses they have been accustomed to for decades.
The enormous growth of the internet as a form of research and alternative shopping has begun to drive these industrial markets to seek online alternatives. Many are learning they have been losing thousands of dollars over the past 20 years by seeking no other alternative. Now many are taking a chance.
“It really is an exciting time,” states Craig Chamberlin, marketing manager of VFDDistributing.com, “many of our customers are reluctant to try alternatives because they assume online businesses will not provide the quality of service they find in their local shops. Now we have an opportunity to show we’ve stayed successful for 20 years by looking out for our customers.” VFDDistributing.com offers online drive sales but they are expanding all their services to their online customer base.
Excited, Craig states,“If they give us a chance, we can show them that we are extremely experienced in working in the field and offering extremely competitive pricing.” Their parent company, Precision Electric, is a one stop shop for everything ranging from Motor Repair to Panel Building and Complete Automation. All of these services which are made available to the customers they make online.
People are excited about it. Industries such as OEMs, industrial manufacturing, food, wood and steel processing, automation have a new way to cut costs, save time, and have the technical support they deserve. One customer says, “All I did was a google search looking for a particular piece of equipment I was looking for, and many choices came up, it’s definitely a more competitive world out there for our vendors. If they aren’t paying attention and staying competitive, they are going to lose alot of work.”
There are a long line of reasons customers are seeking internet for purchasing and repair work in the industrial world. Many argue that not only is it the issue of price, but also technical support as well as repair and service work. Many local vendors have had these customers trapped into a corner for so long, local repair centers have lost their excellent customer service and support which they once targeted these customers with.
Precision Electric, Inc. and VFD Distributing is a family owned business that offers excellence in industrial support and service work, and have been doing so since 1984. Simply inquire for a free quote or if you are in need technical support.
Machinery imported into the United States is often rated at an operating frequency of 50 Hertz.Unless engineered for operation at 60 Hz., this can be problematic for electric motors. This is especially true when operating pump and fan loads.Too often the distributors and purchasers of this machinery assume that the Original Equipment Manufacturer has taken this into consideration.In the repair business we frequently realize this when motors are received for repair roasted out from overload.
AVariable Frequency Drive(VFD) can be used to properly address the issues associated when operating 50 Hz equipment at 60 Hz.
Motor speed is directly proportional to the operating frequency.Changing the operating frequency on a pump or fan increases the operating speed, and consequently increases the load on the motor.A pump or fan load is a variable torque load.A variable torque load varies by the cube of the speed.
A 50 Hz motor operating on 60 Hz will attempt to rotate at a 20% increase in speed.The load will become1.23 (1.2 x 1.2 x 1.2) or 1.73 times greater (173%) than on the original frequency.Redesigning a motor for that much of a horsepower increase is not possible.
One solution would be to modify the driven equipment to decrease the load.
This may include trimming the diameter of the fan wheel or impeller to provide the same performance at 60 Hz as the unit had at 50 Hz.This will require consultation with the equipment manufacture.Possibly the same manufacture who chose to install 50 Hz rated on a machine to operate on 60 Hz.(your confidence in them should already be suspect).There are other considerations associated with an increase in speed besides the increase in load.These include mechanical limitation, vibration limits, heat dissipation, and losses.
The best solution is to operate the motor at the speed for which it was designed.
If that is 50 Hz., then avariable frequency drivecan be installed.These drives will convert the 60 Hz line power to 50 Hz at the motor terminals.
There are numerous other benefits that will be realized with this solution.These benefits include:
- improved efficiency
- power regulation (often better than the utility will supply)
- motor over current protection
- better speed control
- programmable output to perform other tasks
- improved performance.
The same load formula above can be used when speed of a variable torque load is reduced using a Variable Speed Drive.Therefore a 20% decrease in speed will require 58% of the original Horsepower.
Many electricians applyVariable Frequency Drives (VFDs)toAC Motors that are not inverter rated. Manyare not even aware that inverter rated motors exist.
Inverter rated motors are not required for inverter applications, however, when aVFD is applied to an inverter rated motor, the inverter rated motor has less chance of premature winding failure. Inverter rated motors have unique windings designed for voltage spikes up to approximately 1500 Volts.
Variable Frequency Drives (VFDs) create artificial sine waves which allow an AC Motor to function; normal AC Motor windings are designed for voltage up to around 600 volts. When these spikes exceed the maximum, the winding insulation starts to break down and eventually will burn up. Inverter rated motors are optimized with higher rated insulated (pulse-shielded) copper windings.
These type of windings can handle voltage spikes up to 1500 volts and higher beforethe insulation will begin to break down. Inverter rated motors also have tighter bearing air gaps than normalAC Motors. Thesetighter air gaps are designed to prevent voltage buildup in the proximity of bearing housings which can cause bearing failure.
The greater the distance the motor is from the drive the more profound the effects of inverter generated voltage spikes. When the wire from an inverter to the motor is 50 ft or longer, an Inverter rated motor should always be applied. Always chose an inverter rated motor on new applications.
Operating a Non-Inverter rated motor with an inverter will void the warranty. When the warranty claim is evaluatedby a qualifiedservice shop and/or manufacturer, they will determine the cause of failure to be Operating of a Non-Inverter rated motor with an Inverter.
Consult with a professional prior to making a decision on what type of motor to use in yourVFD application. Many customers tend to use an existingAC motor for the VFD application if the motor is already available, and replace itwith an inverter-rated motor when the original motor fails. There is some risk in this practice should the failed motor damage your new inverter.
The general lifespan of anAC Motor is dependant on several factors such as:
- Routine Maintenance
- Using the correct type of motor andVFD for application.
Many electricians today apply Variable Frequency Drives (VFDs) for numerous reasons on AC Motor applications. One advantage of using aVFD is to extend the lifespan of anAC Motor.VFDs allow soft-start which in turn creates less wear and tear on a motor, however, if the motor being applied is non inverter rated, some of these benefits may not apply.
This does not mean you should only use aVFD on inverter rated motor only, this just means you have overall greater benefits on inverter motors than basicAC motors.
A properly applied VariableFrequency Drive (VFD)will significantly reduce operating costs. This is particularly true for variable torque loads such as:
Blowers, for example, are often used with dampers to control air flow. These dampers may be operated either manually or automatically. When dampers are closed, 50% motor current will drop to approximately 60% of Full Load nameplate current. By utilizing aVariable Frequency Drive (VFD)in this application, current draw in the motor will be reduced 30% for every 10% drop in speed. The same motor operating froma Variable Frequency Drive (VFD)at 50% speed will draw approximately 20% of FLA.
An example application:
A 10HP AC motor rated 90% efficient running across the line with the dampers operating between 50 70% for 2000 hours per year will require 11,996 KWH. If your KWH charge is $.08 per KWH, the cost to run this motor will be: $1,248.00 annually.
The same motor operating from an ASD between 50 70% speed for 2000 per year will require 4,676 KWH. Operating cost at the same KWH rate will be: $ 432.00 per year. This represents a savings of $ 816.00 per year and should be enough to pay for the investment into a drive and installation costs in the first 12 months of operation.
Ifthe application operates more hours than in this example and/orthe KWH charge is higher the savings will compound very fast.
Another factor to consider is mechanical wear. Because the motor and blower in this application is running at a lower speed mechanical wear will be proportionally less. You should also expect less vibration and heat that may affect other equipment nearby.
Most VFDs will accept a 4-20 Ma input signal for speed reference and control. Most pressure transducers and automatic controllers can be wired directly into the same control position as your automatic damper. (also 4 20 ma)
The same theory will apply to all variable torque loads. A variable torque load is one that the load on the motor shaft increases when speed increases, or decreases when the speed decreases.
One of the more common problemsseen in ourVariable Frequency Drive (VFD) repair division is the failure oftheIGBT (Insulated Gate Bi-polar Transistor)power section modules.
If theVariable Frequency Drive (VFD) is blowing fuses, or theVFD simply is not turning on, the followingtest may aid you in finding the root of the problem.
A digital voltmetertest cantellifa short existsfrom the input side of yourIGBT power section modulesto the output side without having to take the wholeVFD apart to inspect them.An alternative, more costlytest is done by simply replacing the fuses that have blown, then turning the power on.This is costly because if the short exists, after turning on the power you can expect a boom that will hit you yet againfor$100.00 fuses.The digital voltmetertest could savemoney, fusesand the embarrassment of aVFD blowing up in your face.
Digital Voltmeter on Diode Test:
Every ACVariable Frequency Drive (VFD) has a sectioncalled theDC buss. This section is the output oftheIGBT‘s.The terminals are oftenlabeledDC+ and a DC-. The preliminary requirements to the Digital Voltmetertest include:
- Locating the DC+ and DC-terminals ontheVFD. They are usually located near the input and output terminals.
- Locating your input and output terminals, and if you located your buss already you have found these terminals.
- Make sure that there are no input or output leads connected to theVFD because this will effect the readings on your meter.
Now thatthe right terminals have been located, proceed with the following steps totest theIGBT power section:
- Turnthe voltmetersettings toDiode check. It looks like this ->I-
- Takethe positive lead on the voltmeter and put iton the DC- terminal of theVFD.
- Now takethe negative lead and put it on each input and outputterminal of theVFD one at a time.
- If a terminal is good,it should returnanywhere from a0.299 volt to a 0.675 volt reading onthe meter.
- Nowrepeat the sameprocess the opposite way.
- Takethe negative lead and put it on the DC+ terminal.
- Now takethe positive lead and put it on each input and output terminal of theVFD.
- Again,one shouldexpect the same readings as in step 4.
- Ifthe meter returnsa reading of 0.000 – 0.100,theIGBT is shorted and needs changed.These readings could result in blown fuses or even morecostly damages.
- Ifthe meter returns a readingof more than 0.750, it is possiblethe contact is open or there could be other devices with issuesbetween theIGBT andtheterminal. If this is the case one should contact their local electronics repair shop or contact us during our store hours to resolve the issue.
There are many things that can go wrong withVariable Frequency Drives (VFDs). The failure of theIGBTpower section is one of the most common.Educating yourself and understanding how the technology works is the first step in saving both you and your company money. Often times, you will find the electronics repair shop who does work for you will appreciate the preliminary troubleshooting you have done beforeyou called. This can result in less cost to you and less diagnostics work for them.
Engineering technicianshave many nightmare stories when it comes to on-sitetroubleshooting. In this instance, I wascalled to helptroubleshoot a Closed Loop (Sensorless Vector)Variable Frequency Drive (VFD)on a production line that was so large, itseemed to goso far down the plant, it never ended.
Afterovercoming theintimidationassociated withthe sheersize of the line, it became a question of focusing on just theVariable Frequency Drive (VFD)causing the issue. The maintenance technicianson sitenot only had home court advantage, but were on the phone with the Original Equipment Manufacturer (OEM) technical support. Everything on the line ran great, right up to the pointwhere theVFD on thenetwork in question was supposed to start turning a set of rolls.
TheVFD was a proprietary brandthat was made in Japan with the rest of the machine. After speaking with technical supportfrom Japan,a list of discrete inputs to the Programmable Logic Controller (PLC) on thenetwork were determined that could be checked. The maintanceguys at this site were pretty sharp so they had already checked the same list twice.It is still good practice when troubleshooting these types of problems to check these discrete inputs.
The problem most have withtroubleshooting aVariable Frequency Drive (VFD)controlled by anetwork is that it seems so intangible. There are no wires going to the start terminal to throw a meter on. ThisVFD, likemost others, had a keypad on its front. These circumstances brought aphrase to mind that was often published on the cover of Love temperature controllers stating, “If all else fails, please read these instructions.” The customerhad a manual on theVFD, looking to the manual is always agood first stepto discovering the root of the issue.
When troubleshooting communications between aVFD and a PLCon thenetwork it is necessary to look at theVFD‘s “read only” parameters and look for the answers to these two important questions:
- IstheVariable Frequency Drive (VFD)getting a run comand?
- IstheVFD getting a speed referance?
After getting familiar with the keypad, the customer was requested to get the machine running again.With the information learned from the manual, through the keypadit was determined theVFD was getting a run command and was, in fact, going into run.
However, it was also discovered that the speed reference was running at0%. Normally a speed reference on aVFD will run between 0% and 100%. So in thisinstance, it was running at0%. So theVFD was running great at 0speed, but 0 speed is not moving.After discussing it over the phone withthe OEM technicalsupport,it had turned out the rung within the PLC on thenetwork turning on the speedreference was not giving the proper speed reference to theVFD. Now the customerhad something to work with and were able to resolve the issue through the PLC.
Keypads can be very useful whentroubleshooting Variable Frequency Drives (VFDs)controlled bynetworks. Sometimes it is just a question of getting familliar with the way each uniqueVFD handlesnetwork communications.
Often times those using a Variable Frequency Drive (VFD) may find themselvesneedingto connect a higher horsepowerVFD to asingle phase input power source.Since most higher horsepowerVFDsonly acceptthree phaseinput as a power source, they are left with little options or alternatives.Don’t fret, there is a solution.
If you are using a Variable Frequency Drive (VFD)rated forthree phase input and the only power source you have available to you issingle phase input, then you canderate theVariable Frequency Drive (VFD)to accept thesingle phase input power source. You can almost always use a VFD rated forthree phase input with asingle phase input power source. Of course, if it is available, try touse asingle phase input rated VFD if your power source is single phase.
When only athree phase input VFD is available,it is acceptableandcommon practicetoderate theVFDto work with asingle phase input power source.Variable Frequency Drive (VFD)availability and installation procedures may vary from one manufacturer to another.
Before youderate yourVFD, it is most important to ensure theVFD you are using is properly suited for your application. The following are some basic guidlines to help you in determining whether or not your Variable Frequency Drive (VFD) is suitable for your application:
- Gather motor nameplate data including horsepower (HP), current (Amps), motor voltage, input line voltage andpower sourcephase.
- Determine which type ofVFD your application will require. The type will fall under the category of eitherVolts per Hertz (V/Hz), closed-loop vector, or open-loop vector (Sensorless Vector).
The internal components of thethree phase input Variable Frequency Drive (VFD)is rated for the appropriate current expected whenthree phase input power is applied. When usingsingle phase inputinstead, the line side current from the single phaseis always higher.To “derate”is the process ofensuring that these component are rated for the higher current that will flow from thesingle phase input instead of thethree phase input.
You canderate aVFD by:
- Determining the Horsepower of the Motor theVFD will be connected too, then
- ChoosingVFD with a Horsepowerhigher than the Horsepower of the motor to compensate for the additionalinput currentfrom the single phase power source.
The simplest formula usedfor these types of applications is:
VFD Input Current > Motor Current Rating * 1.73
TheVFD input current must be equal to or greater thanthe Motor Current Rating * 1.73.
When installing mostthree phase input Variable Frequency Drives(VFDs)on an application wheresingle phase input power is used, you will almost always connect the input line leads to L1 and L2 of theVFD. L3will be left open with nothing connected. Consult with theVFD manufacturer or knowledgeable integrator to be sure.
Example ApplicationtoDerate aThree Phase Input Variable Frequency Drive(VFD) to work with aSingle Phase Input power source:
An application has a 230VACsingle phase input power sourceand needs to connect it to aconveyorthat has a Variable Frequency Drive(VFD) connected to a 10Horsepower 230 VAC 3 phase induction motor.Let us assumeit has been determined that this application willoperatewell with a simple Volts per Hertz (V/Hz)VFD.The issue is, since there are noVFD manufacturersthat offer a 10Horsepower (HP)single phase input Variable Frequency Drive (VFD),we will need toderate aVFD with athree phase input forsingle phase input. Most manufactuers ofVFDs only offer products up to 3 Horsepower (HP) forsingle phase input,three phase output; some products such as AC Tech SCF series do offer standardsingle phase input,three phase output products available up to 5 Horsepower (HP) range.
The10 Horsepower (HP)AC motornameplate reveals that the motor is rated for approximately 27 ampsat 230 VAC.We must use theequation above:
- VFD Input Current > Motor Current Rating * 1.73
- VFD Input Current > 27 Amps * 1.73
- VFD Input Current > 46.71
Now it has been determined this application will need a 230 VAC 3 phaseVolts per Hertz (V/Hz)Variable Frequency Drive (VFD) with an input current rated at orabove 47.0 amps.
Our company’sVFD of choice is theAC Technology/LenzeSMVector (SMV) product. Although thisVFD is open-loop vector capable andthis application only requires a standard Volts per Hertz (V/Hz)VFD, the AC Tech SMVector (SMV)VFD is agreat alternative to any manufacturer ofVolts per Hertz (V/Hz)products because the SMV is often the same price or cheaperas any other Volts per Hertz (V/Hz) product andcan operate in eitherVolts per Hertz (V/Hz) mode oropen-loopvector. TheseVFDs are also available in both Nema 1 and Nema 4x enclosures.
Looking into the product catalog, we find an SMV model fitting the requirementsavailable rated at15Horsepower (HP) that has a230 VACthree phase input rated for 48 input amps.
Interesting linksHere are some interesting links for you! Enjoy your stay :)
- 2014 Industrial Services and Training Expo Registration!
- 2015 Industrial Services and Training Expo Registration
- About Us
- AC Drive Repair
- AC Motor Repair
- AC Servo Drive Repair
- AC Servo Motor Repair
- Application For Open Account
- Approve Quote & Checkout
- DC Drive Repair
- DC Motor Repair
- Indiana’s First EASA Accredited Industrial Repair Facility – Precision Electric, Inc.
- Join Us For ISATE 2019 – The 2019 Industrial Services And Training Expo
- Join Us For The 2014 Industrial Services and Training Expo
- Join Us For The 2015 Industrial Services and Training Expo
- My Account
- New Request Form
- PCB Repair
- Precision Electric Industrial Services and Training Expo Registration
- Precision Electric, Inc. – Buy AC VFDs & DC Drives
- Precision Electric, Inc. – Buy Drives, Motors, Phase Converters & More
- Precision Electric, Inc. – Buy EMC, Harmonic, dv/dt & Output Sinewave Filters
- Precision Electric, Inc. – Buy Line & Load Reactors
- Precision Electric, Inc. – Buy Rotary & VFD Phase Converters
- Precision Electric, Inc. – Buy Variable Frequency Drives Online
- Precision Electric, Inc. – Mishawaka, IN 46544
- Precision Electric, Inc. Buy AC Motors
- Precision Electric, Inc. Machine Shop Services
- Print A Repair Packing Slip
- Print A Repair Packing Slip Existing Customer
- Professional Nationwide AC DC Servo Motor & Drive Repair
- Pump Repair
- Register For Our 5th Annual Industrial Services And Training Expo!
- Request An Open Account With Precision Electric
- Request Industrial Equipment Quotation
- Request Product Return Authorization
- Request Product Warranty Authorization
- Return Policy
- Search Results
- Step 2: Ship Your Item, We E-Mailed you A Packing Slip
- Submit A Support Ticket
- Support Request
- Terms And Conditions
- Testing Header User Agent Data
- Thank you for your inquiry!
- Thank You For Your New Product Inquiry!
- Thank You For Your Question
- Thank You, Please Check Your E-mail.
- Track your order
- VFD Training Academy: Professional Online Drive Video & Workshop Lessons
- Warranty Repair Request
- While You Were Out
- Request Industrial Repair Quotation
- Technical Manuals
- Contact Us
- About Us
- ABB ACS355
- ABB Drives
- AC Motor Speed Controllers
- AC Tech SMVector
- EATON SVX9000
- FAQ Automation
- FAQ Electronics
- FAQ Motor Shop
- FAQ VFDs
- Field Experiences
- HT SMVector VFD
- HT VFDs
- Machine Shop Videos
- Product Manuals
- Service Offerings
- Servo Motors
- SMVector Drives
- SMVector Series
- Training Videos
- Video Series
- June 2021
- October 2020
- August 2020
- July 2020
- November 2019
- October 2019
- August 2019
- July 2019
- June 2019
- May 2019
- April 2019
- February 2019
- January 2019
- December 2018
- November 2018
- October 2018
- August 2018
- July 2018
- June 2018
- May 2018
- April 2018
- March 2018
- February 2018
- January 2018
- December 2017
- November 2017
- October 2017
- September 2017
- August 2017
- July 2017
- June 2017
- May 2017
- April 2017
- March 2017
- February 2017
- January 2017
- December 2016
- November 2016
- October 2016
- September 2016
- August 2016
- July 2016
- June 2016
- May 2016
- April 2016
- March 2016
- February 2016
- January 2016
- December 2015
- November 2015
- October 2015
- September 2015
- August 2015
- July 2015
- June 2015
- May 2015
- April 2015
- March 2015
- February 2015
- January 2015
- December 2014
- November 2014
- October 2014
- September 2014
- August 2014
- July 2014
- June 2014
- May 2014
- April 2014
- March 2014
- February 2014
- January 2014
- December 2013
- November 2013
- October 2013
- September 2013
- August 2013
- July 2013
- June 2013
- May 2013
- April 2013
- February 2013
- January 2013
- December 2012
- November 2012
- October 2012
- September 2012
- August 2012
- July 2012
- June 2012
- May 2012
- April 2012
- March 2012
- February 2012
- January 2012
- December 2011
- March 2011
- February 2011
- January 2011
- December 2010
- November 2010
- October 2010
- April 2010
- March 2010
- February 2010
- January 2010
- December 2009
- November 2009